Basics of steam coil and face and bypass operation
Many air handling units in colder climates are equipped with steam heating coils. These coils use control valves to modulate the flow of steam to the coil. Due to the low mass of water in a steam coil, it has a higher propensity to freezing when conditions are right. One of the neat ways we’ve design around this is to use a Face and Bypass (F&B) damper arrangement to allow the coil to have maximum steam flow to prevent freezing. The F&B dampers direct a portion of the airflow through the steam coil and another portion bypasses the coil in order to achieve the necessary discharge air temperature and prevent a freezing airstream from damaging the steam coil. Pretty neat, huh?