In my previous post How to do BAS Graphics Right: Part I, I wrote about the 5 basic rules to BAS graphics I learned during my years as a controls system master integrator. If you’ve not read that post yet, I’d encourage you to go back and give a glance as it’ll put the rules below into perspective, and feel free to ask a question if you got one using the comment section at the bottom of the post. Here’s a quick recap of the rules:
9 min read
How to do Building Automation System (BAS) Graphics Right: Part II
Topics: New Construction Existing Building bas building automation system Controls upgrade
3 min read
Common VRF Issues Part II: Controls
In my first blog on Common VRF (Variable Refrigerant Flow) Installation Issues I focused on issues during mechanical and hardware installation that typically lead problems during startup and pre-functional checkout commissioning. This blog will focus on controls issues identified during commissioning design review which usually lead to issues during start up if not addressed up front during design. As mentioned in the previous article, VRF systems can allow for better comfort and overall satisfaction, but if not properly programmed for the owner’s specific application, can lead to numerous complaints during the first year of occupancy.
Topics: commissioning New Construction Controls upgrade design review
11 min read
How to Do Building Automation System (BAS) Graphics Right: Part I
Over the course of my career I have evaluated BAS graphics packages as a function of my daily 9 – 5. I have been doing this since 2002 and in those days, most BAS manufacturers barely had functioning websites. However, the products they sold allowed their vendor networks to create Human Machine Interfaces (HMI) and Graphical User Interfaces (GUI), and these interfaces haven’t really functionally changed a whole lot since those days of pre-broadband internet and before the smartphone was commonplace. Given that we may be stuck with outdated user interfaces for some time to come, it makes it all the more important that proper care is given to how the information is displayed and to ensure users can easily absorb the information they need from the BAS.
Topics: commissioning Building Data New Construction Existing Building bas building automation system Controls upgrade
3 min read
Making Sense of Building Data: Part 1: Overview
Similar to other domains, data from buildings is being generated at an unprecedented pace and scale. However, all of that data is useless if we can’t extract meaning to create value and yield actionable insights. This requires the utilization of protocols or standards to effectively make sense of the data. Project Haystack is one such standard that has been developed over the past several years and allows for the contextual tagging of data in a flexible way, using data from any number of sources.
Topics: Building Performance & Technology technology Building Data Energy Management Controls upgrade energy monitoring & solutions
3 min read
Occupant Based Controls for Energy Savings
I recently attended the Performance Evaluation Methodology for Building Occupancy Sensing Systems for HVAC Controls workshop, which followed the annual ASHRAE conference that just wrapped up in Kansas City, MO. The workshop focused on one of ARPA-E’s research programs called SENSOR (Saving Energy Nationwide in Structures with Occupancy Recognition), and brought together a diverse group of individuals, including researchers from national labs and universities, industry representatives, design engineers, and other interested parties.