Cx Associates provided peer-level design and construction phase commissioning of the mechanical, electrical, and plumbing systems for the YMCA's new, state-of-the-art facility in Burlington, VT. The building is made up of a gymnasium, natatorium, studios, fitness areas, childcare spaces, and offices, and uses water source heat pumps for heating and cooling with rooftop units (RTUs) and an HRV for ventilation. Our work focused on efficiency, first-cost and maintenance cost savings, and ensuring occupants would be comfortable in their spaces. For example, we found a lighting controller that required a fifteen minute wait time before the lights could be re-enabled after shut-down, a potential safety hazard. We worked with the design team and the contractors to find solutions to this and many other issues.
CxA’s commissioning of the multi-purpose, year-round Stowe Arena began during the Request for Proposals (RFP) stage and continued through bidding, design, construction, and occupancy. The RFP development and bidding services helped to ensure that energy efficient design concepts were included in the project proposals from the very beginning. During the design phase, CxA identified many opportunities to improve building performance, such as variable speed control for the desiccant dehumidification system, and optimal hot water supply temperature for boiler efficiency and heat recovery. CxA’s functional performance testing of the installed systems revealed additional opportunities to improve energy efficiency, such as reduced ventilation air pre-heating and adjustments to lighting control settings to more effectively switch off lighting when spaces are unoccupied.
Cx Associates was retained by the Town of Shelburne, VT to provide design and construction phase commissioning for the town’s 16,000 SF new Pierson Library and renovated Historic Town Center project. Commissioned systems included the heating, ventilation and air conditioning system (HVAC), domestic hot water, and lighting and lighting controls. Designed with sustainability and high-performance in mind, the building incorporates many energy efficiency features such as a roof rainwater collection, passive daylighting, and energy-efficient HVAC equipment. Designed for net-zero energy use, the new library and town center was awarded the 2020 Efficiency Vermont Best of the Best Honor Award – Large Commercial, as well as the 2020 People’s Choice Award at Efficiency Vermont’s Better Buildings by Design Conference.
Cx Associates has provided design and construction phase commissioning projects for several large Vermont Army National Guard projects. These projects include the following:
Cx Associates provided design, construction and occupancy phase commissioning services to VTANG’s new LEED Gold Certified Security Forces Building. We commissioned mechanical and electrical systems, including ground source heat pumps and solar PV. Our commissioning engineers found several issues during construction phase, such as sensors installed too high and poorly programmed controls sequences. We estimate that the resolution of these issues saved the facility $7,000/yr. in energy and maintenance costs.
From 2016-2018, Cx Associates provided construction and post-occupancy commissioning services for a new Flight Simulator Building (Building 120) for the Vermont Air National Guard in South Burlington, VT. For this project, Cx Associates focused on the HVAC systems and identified issues pertaining to the duct access doors, a broken damper shaft, improperly aligned air vents, damaged heating coil fins, and a number of other systems.
Topics: commissioning New Construction Military
Cx Associates provided lead commissioning services for a LEED Gold certified renovation and expansion of VTANG’s Fire-Crash-Rescue facility in South Burlington, VT. Our commissioning work with this high-performance building included mechanical and electrical systems, air and water source heat pumps, a geoexchange wellfield, and a 27.63kW PV array on the roof of the station. We developed and coordinated a Measurement and Verification Plan in compliance with LEED-NC 2.2 credit EA C5 to monitor all energy consuming systems through a DDC Base Meter Monitoring System (BMMS).
Cx Associates provided construction phase commissioning services for this new construction project in Burlington, VT, which features office space and 20 residential apartments. The project utilized high efficiency water source heat pumps to offset their heat/cooling rejection in the swing seasons, thereby minimizing the energy input from the central plant during those times. We identified approximately 100 issues during project construction; for example, we found that no automatic controls were installed on exterior lights and no emergency shutoff switches were installed for the gas-fired boilers. We recommended changes that saved the client energy, first costs, and long-term maintenance costs.
Topics: commissioning Multifamily New Construction
Cx Associates provided design, construction, and occupancy phase commissioning for Housing Vermont and Downstreet Housing & Community Development’s new 30-unit multifamily building in Montpelier, VT. Our clients' commitment to providing affordable housing to Vermonters means they needed a commissioning provider who would ensure the new building operated efficiently and with low maintenance costs.
Cx Associates provided mechanical and electrical commissioning for this new county nursing home in Boscawen, NH. This multi-residential health care facility includes over 300 beds, kitchen, laundry, offices and ancillary spaces. The owner required commissioning as a mandatory component of the project to ensure that all systems were complete and functioning properly upon occupancy, and that adequate documentation and training were provided to facilities staff. The facility design included energy efficient measures such as radiant floor heating, geothermal heat pumps, and energy recovery ventilators.
Cx Associates provided commissioning services for the construction of the Spruce Peak Adventure Center at Stowe Mountain Resort. We completed an in-depth review of the HVAC controls design and contractor’s scope work to identify and close existing gaps, resulting in a final, clear, agreed-to path forward for implementation of a complex controls package. As a result of our successful work on this project, we have been retained for several problem-solving projects with Stowe Mountain Resort.
Cx Associates provided commissioning services for this new waterfront boutique hotel which holds 126 guest rooms. Our early involvement in the project allowed us to identify design improvements that resulted in improved building performance and energy cost savings such as $10,000 first cost savings from a lower cost roof to air handling unit, 63,000 kWh and $8,000/year from variable speed pump installations, and 1,750 CCF and $2,500/year from separating the domestic hot water from the heat pump loop heating.
Cx Associates continued working with Hotel Vermont after occupancy to develop and test a new sequence of operations for the existing energy recovery unit (ERU) to reduce energy use and improve occupant comfort; this work was a direct result of observations made during the commissioning process.
Cx Associates provided Construction and Occupancy Phase Commissioning services for the Rutland Housing Authority (RHA) and Housing Vermont’s multifamily building in Rutland, VT. Working as the independent commissioning agent, we delivered a quality assurance process to help ensure the project meets the High Performance Track of the Efficiency Vermont Multifamily Energy Standards for New Construction. In order to meet this goal, our services for the project included construction verification, functional performance testing, maintaining a commissioning issues log to work through identified issues with the project team, training support for O&M staff, and a review of the systems manual. Ten months after building occupancy, we performed a follow-up visit to ensure that the systems were continuing to operate as designed and installed.
After providing commissioning services for ECHO, Vermont’s first LEED certified building, in 2003, Cx Associates provided retrocommissioning (RCx) services for ECHO in 2014. We provided services to help ECHO achieve their goals to improve the performance of their pumping and air systems. In addition to reducing the operations staff-time required to maintain the building, the measures we identified included savings of 64,150 kWh annually across a couple of upgrades and improvements.
Cx Associates managed and conducted a full commissioning quality assurance and validation process for the new Vermont Hard Cider bottling facility. During our rigorous validation process, we uncovered several significant construction issues that, had they not been corrected, may have resulted in significant equipment failure and waste. Cx Associates identified dozens of opportunities to both increase operational effectiveness of the facility as well as energy efficiency.
Cx Associates provided commissioning for the renovation of the historic building that is used as Middlebury College’s president’s residence. The building has been recognized for its energy efficiency, winning Efficiency Vermont’s top award for a major renovation of a commercial building. As a result of our early involvement in the project, we were able to identify an opportunity for the engineer to modify sequences and piping to ensure the heating boiler was not damaged by missing logic. Our follow up on the issue resolved a lack of communication that could have resulted in a voided boiler warranty.
Cx Associates provided commissioning for the new squash center on Middlebury College’s main campus, which includes nine squash courts, an entrance to the main athletic complex, and seating for hundreds of spectators. Cx Associates was retained to assist in the pursuit of LEED certification for the project. Commissioned systems included HVAC, domestic hot water, and lighting and lighting controls. Our early involvement during the design phase allowed us to develop close relationships with the college and the contractors which helped ensure the controls for the ventilation system and lighting system met the design intent and needs of the college.
Cx Associates provide design and construction phase commissioning for Middlebury College’s new Field House. Our review uncovered several issues that, when corrected, reduced first cost and increased energy efficiency. During the construction phase, we corrected over 50 issues with the rest of the team, each found during commissioning. Correcting these problems improved equipment access and maintainability, improved sequences of operation and other equipment programming, and resulted in improved environmental quality.
Cx Associates provided commissioning during Champlain College’s two-phase dormitory project to build three new residence halls on their campus. Our work ensured that the buildings conformed with the project Owner’s Project Requirements (OPR), Basis of Design (BOD), and contract documents. The project included energy efficient design elements such as heat pump systems connected to a ground source wellfield serving a multi-building district.
Cx Associates provided commissioning services for Construction and Post-Occupancy phases of this multi-building project. The overall project was comprised of three separate projects: the ICU/Medical-Surgical addition, which included twenty new single occupancy patient rooms; the main entrance and lobby renovation, which included the outpatient clinic addition and contained multiple exam rooms; and a new standalone medical office building.